Source: MA-OpenDSS Version 1.3 User Manual

https://www.ece.ucf.edu/~qu/ma-opendss/

Generic5 is a generic model for inverter based DG, which has an open form of control feedback and can be control either locally or from network. An example model is as bellow:

 Property Description Bus1 Bus to which the Induction Machine is connected.  May include specific node specification. Ctrl_mode Define the contrl modes. For example:  (1)        ctrl_mode =0: Three phase DG sequence control; ctrl_mode =1: Single phase DG, control is on Phase A; (2)        ctrl_mode =2: Single phase DG, control is on Phase B; (3)        ctrl_mode =3: Single phase DG, control is on Phase C; (4)        ctrl_mode =4: Three phase DG, control is on Phase C; kcd The local control gain on real power. kcq The local control gain on reactive power. kv Nominal rated (1.0 per unit) voltage, kV. For 2- and 3-phase machines, specify phase-phase kV. Otherwise, specify actual kV across each branch of the machine. If wye (star), specify phase-neutral kV. If delta or phase-phase connected, specify phase-phase kV. kW Shaft Power, kW. Output limit of a DG P_refkW Ref P Value (kW). P_ref has prority to kW which is nominal value. (Incide variable P_ref is W) V_refkVLN Reference Voltage. V_ref (Unit kV, L-N value) work only when QV_flag=1 Volt_Trhd Threshhold for voltage control. 0.~0.05. 0 means v has to follow v_ref Q_refkVAr Reference Q Value: work only when QV_flag=0 QV_flag QV_flag : 0-Q_ref mode; 1- V_ref mode CC_Switch CC_Switch = true: network level control is on; CC_Switch = false: network level control is off.

Examples

New Generic5.g1  bus1=76  phases=3  kVA=2100  kV= 4.16  kW=1750  P_refkW=10  V_refkVLN =2.402  Q_refkVAr=0  ctrl_mode=0  QV_flag=1  kcd=0.2  kcq=2 Volt_Trhd=0.01  cc_switch=f

New Generic5.g2  bus1=83  phases=3  kVA=2100  kV= 4.16  kW=1750  P_refkW=10  V_refkVLN =2.402  Q_refkVAr=0  ctrl_mode=0  QV_flag=1  kcd=0.2  kcq=2 Volt_Trhd=0.01  cc_switch=f